Shipsan Potable Water Treatment 4 x 5 Litres. It can be used in tank and pipe sterilisation and for spray application super-chlorination as well as a potable water treatment if a risk has been identified specifically it can be used in case of emergency treatment on board of the domestic/drinking water if the supply is found to be sub-standard. It is faster acting and much more effective than sodium-hypochlorite.
Super-chlorination using Shipsan® – Spray Method – fast and efficient
Radically reduces the procedure time • Huge saving in Disposal Costs • Saves valuable ship time
It is ideal for use in water hygiene storage tanks and pipe work treatment applications, where it quickly eradicates
Legionella, Pseudomonas and other microbes. Available in 25L, 200L, 1,000L IBC’s.
Tank clean (MGN 397); “To be opened up, emptied, ventilated and inspected and thoroughly cleaned, recoated
as necessary, aired and refilled with clean freshwater chlorinated to a concentration of 0.2ppm free chlorine. The
cleaning process should include disinfection.”
1 Clean and rinse the tank and pump out residue.
2 Dilute 1 litre Shipsan to 20 litres of deionised water (200 ppm free-chlorine).
3 Spray all surfaces with Shipsan® (diluted as above) and leave for a few minutes to Superchlorinate/Disinfect.
4 Rinse the surface and pump out residue.
5 When using Shipsan spray method for super-chlorinating the freshwater tanks consideration should be given to the distribution system;
Using a Hydrophore system: The hydrophore tank requires a solution of 200ppm (Measured as Free Chlorine) Shipsan is then used to sanitise the distribution
system, operating all outlets to ensure the chlorination is achieved at all points, followed by flushing after 30 minutes. (200ppm Shipsan = 1 Litre Shipsan to 20
Litres de-ionised water).
Positive Pressure Pump System:
Using a positive pressure pump system direct feed from the fresh water tank.After Super-Chlorinating the fresh water tank using Shipsan as above procedure,
use a cofferdam to supply the pump inlet pipework should be filled with a solution of 200ppm (Measured as Free Chlorine) Shipsan to be used to sanitise
the distribution system, operating all outlets to ensure the chlorination is achieved at all points followed by flushing after 30 minutes.
(1 Litre Shipsan to 20 Litres de-ionised water).
6 Refill the tank to achieve typically 0.2ppm – 0.5ppm. (As per the levels indicated in your Water Safety Plan) using Shipsan. Test the water for free chlorine.
4 x 5 Litre Pack
It is non-corrosive and has 2 years shelf life minimum as an opened drum.
...if the supply is found to be sub-standard or if you need to treat in view of a positive legionella test. Visit www.shipsan.co.uk
Shipsan Potable Water Treatment 4 x 5 litres
- Product Code: shipsan-potable-water-treatment-4-5-litres
- Availability: In Stock
- Ex Tax: £149.60